Phyn Plus Installation
We recommend that Phyn Plus be installed by a licensed plumber. We can help you find installers that are trained to install the device, or you can hire your own plumber.
Uponor Pro Squad installation
Trust the Uponor Pro Squad with your Phyn Plus purchase and installation to receive an extended warranty, home protect guarantee and more.Learn More
Have your own plumber install
Purchase Phyn Plus online, with free shipping*, and have your own plumber install it for you. We have all the info they will need to know to do a great job.Learn More
Partner with a Pro
We have partnered with the Uponor Pro Squad, a team of elite water specialists, to provide premium installation of Phyn Plus. With the Pro Squad, you’ll have the peace of mind knowing that Phyn Plus was installed properly and get exclusive benefits.
Fill out the form and a Pro Squad installer will reach out to set up a free consultation.
Your Pro Squad installer will visit your home, survey the installation site and provide a quote on installation.
Pro Squad installer will install and set up your Phyn Plus device.
Frequently asked installation questions
Installation typically takes one to two hours, and depends on the location of your main water supply.
We recommend that you use a licensed plumber to install Phyn Plus. The main water line to your home will be cut where Phyn Plus is installed. We have partnered with the Uponor Pro Squad to bring you local plumbers that have expertly-trained to ensure that Phyn Plus is installed properly, and to meet all local code requirements. You can also use your own licensed plumber.
Yes, you can use your own plumber to install Phyn Plus. We have included instructions that you can give to them in the Phyn Plus box. They must follow these instructions carefully to ensure proper installation.
The maximum working pressure is 125 PSI.
Yes. You will need an electrical outlet within 15 feet of where the device is installed (we recommend a GFCI equipped outlet). Phyn Plus comes with a 15-foot power cord.
Phyn Plus has a 1” NPSM male threaded end on both sides of the device. If you purchase online, we include a 1” to ¾” meter fitting to transition the device onto ¾” pipes.
If you have a fire sprinkler system that is standalone and is on its own branch of pipes (not integrated into the same pipes that deliver water to your fixtures) then Phyn Plus can be installed as long as it is placed after where your sprinkler line branches off. Phyn Plus should not be installed where it will interfere with your fire sprinkler operation.
Phyn Plus is installed on the water main – your plumber will need to cut the pipe to insert it “in-line”. It will be located after your existing shutoff valve and before your plumbing splits off to fixtures or your water heater. Whatever comes “after” Phyn Plus will be monitored for leaks and water use.
Phyn Plus must go after your PRV. If you don’t have a PRV, don’t worry, you don’t need one for Phyn Plus to work.
Typically, irrigation systems are before the PRV, so they can access a higher pressure. If you don’t have a PRV, go ahead and place Phyn Plus before the irrigation or route the main to pick up the irrigation after Phyn Plus. If you do have a PRV, we do not recommend routing pipes so that your irrigation is after the PRV. If you do this, your irrigation could experience a noticeable loss in pressure.
No! Do not solder connections while they are attached to Phyn Plus. This can overheat the electrical components causing them to fail and this will void your warranty.
Absolutely! Phyn Plus has been installed on many homes with wells.
We recommend that Phyn Plus be installed on pipes less than 1 ¼”. Larger pipe diameters may cause the water pressure to be noticeably reduced.
You can reach our installation support team at +1 (877) 749-6792 during normal business hours, Pacific Time.